Can a fire door be used as a normal door?
We’re sometimes asked, incidentally, whether a designated fire exit can also legally be used as a regular entrance/exit door i.e. for every day use. The answer is yes it can – indeed the fact that it is in daily use makes it ideal as an escape route as its location is well known.
Can you fit a fire door to an existing frame?
Fitting new fire doors into existing frames is risky because the existing frame may not be fit for purpose or compatible with the certification of the new fire door leaf.
Can I modify a fire door?
Can I make alterations to a Certifire approved fire door? Yes! You can make some alterations provided they are within the scope of the fire door’s ‘Certifire Approval’ documents (CF). This information is also contained in the installation and maintenance instructions supplied with each door leaf.
What is the difference between a fire door and a normal door?
FD30 fire doors are usually 44mm thick, compared to a standard door thickness of 35mm. Sometimes it is possible to amend the frame to fit the fire door but be sure to check the doors’ fire test evidence, as quite often they specify the requirement for larger frame sections.
Do all fire doors need self closers?
In ‘residential’ type buildings (care homes, hotels, student accommodation etcetera), all fire doors should be fitted with a self closing device, minus those such as cleaner and service riser cupboards, which will be closed behind and generally locked by the user.
What should you never do to a fire door?
Never leave a fire door wedged open
Apart from the obvious consequence of potential loss of life, or injury, and damage caused by a fire spreading throughout a building, it is actually illegal for a fire door to be propped open. As such, all fire doors MUST be fitted with an automatic closing system.
Does a fire door have to have an intumescent strip?
The Building Regulations indicate where you have fire doors, these would require intumescent strips. … If the gap is too wide, it may compromise the door’s ability to restrict the spread of fire and smoke.
What are the requirements for a fire door?
All fire doors should meet the essential fire safety standards: the door must be of FD30 type, offering at least 30 minutes’ fire resistance and have been tested in accordance with BS476: Part 22 1987 (the British Standard) or BS EN 1634-1 2000 (the UK adoption of European standards)
At the top and along the vertical edges there must be a 2 and 4mm gap, while there should be no more than a 10mm gap at the bottom of the door. If the fire door has to be smoke resistant as well as fire resistant (eg FD30s or FD60s, where the ‘s’ stands for ‘smoke resistant’) the threshold gap should only be 3mm.
Can anyone install a fire door?
For fire doors to be an effective method of protection, they have to be not only carefully made but also fitted correctly. … However, there is no formal requirement for people who install fire doors to have any particular qualification or accreditation, so anybody – in theory – can take on the task.
How do you tell if your door is a fire door?
Certification. The most reliable way to identify a fire door is to look for its certification label. All JELD-WEN fire doors will have a certification label on the top edge of the door leaf.
Does a kitchen door have to be a fire door?
For a typical two storey domestic home the Building regulations require that where the property has an integral garage the door between the main property and the garage (normally kitchen or utility) should be a FD30 fire door (30-minute fire resistant) and include smoke seals and self-closing device – it is also …
Can a solid wood door be fire-rated?
Older doors will be made up of solid wood rails and stiles with thin wood panels in between. … This type of door can meet the test for fire ratings up to one hour according to NFPA 252 and is frequently used in fire-rated assemblies in residential and business occupancies.