At the top and along the vertical edges there must be a 2 and 4mm gap, while there should be no more than a 10mm gap at the bottom of the door. If the fire door has to be smoke resistant as well as fire resistant (eg FD30s or FD60s, where the ‘s’ stands for ‘smoke resistant’) the threshold gap should only be 3mm.
The short answer is: there is no general, recommended, or mandatory amount on a fire door that can be trimmed. … This means that the fire door’s test certificate may be void because the door has been altered outside the scope of its certification and its performance may be affected, rendering the door illegal.
How do you reduce the gap under a fire door?
4 Fire Door Checks to Prevent the Spread of Smoke
- Control of Door Gaps. …
- Ensure the Smoke Seal Closes the Gaps. …
- Ensure there are only limited amounts of unprotected region around the door. …
- Make sure the door closer can close the door against the seal.
Can fire door blanks be cut to size?
They are available in numerous sizes but generally speaking are most commonly cut down from 2135x915mm or 2440x1220mm. The fire door blanks are available in 1/2 hour fire rating at 45mm thick and also in a 1 hour fire rating at 54mm thick.
What should you never do to a fire door?
Never leave a fire door wedged open
Apart from the obvious consequence of potential loss of life, or injury, and damage caused by a fire spreading throughout a building, it is actually illegal for a fire door to be propped open. As such, all fire doors MUST be fitted with an automatic closing system.
Are fire doors a legal requirement?
Why do you need to provide fire doors? They are specifically designed to withstand fire for up to 30 minutes. They are a legal requirement for flats which open onto communal areas shared with other tenants. This is to make sure crucial escape routes are protected if a fire breaks out.
Intumescent strips should be fitted into the fire doors frame or lining, where possible. … The gap at the bottom of the door (commonly referred to as ‘the threshold’) is usually around 10mm* for non-smoke conditions BUT 4mm when smoke seals are required.
What should you do if you see smoke coming from under a door?
If you see smoke coming under the door — don’t open the door! If you don’t see smoke — touch the door. If the door is hot or very warm — don’t open the door! If you don’t see smoke — and the door is not hot — then use your fingers to lightly touch the doorknob.
Are fire doors air tight?
As a Fire door is required to form a virtual air tight seal when closed the failure to fit a fire door correctly will compromise the door’s performance and ultimately property and lives will be at risk.
Can you fill a hole in a fire door?
Go to NFPA 80, Fire Doors and Fire Windows (1999 edition), and check out paragraph 15-2.5. … Under that paragraph, you can fill in holes caused by hardware changes by the following methods: Install steel fasteners that adequately fill the holes. Fill the screw or bolt holes with the same material as the door or frame.
Can anyone install a fire door?
For fire doors to be an effective method of protection, they have to be not only carefully made but also fitted correctly. … However, there is no formal requirement for people who install fire doors to have any particular qualification or accreditation, so anybody – in theory – can take on the task.